Asix is set to sync with local pc. T3000 shows that time and date not in sync, but actualy they are. After i press sync I get this:
Then i refresh controler i get this:
Chelsea will check this out. Thanks for the heads up once again Andrius.
Please update latest firmware rev51.6.
may be it is something with daylight saving.
Press SYNC (Daylight on):
Press Refresh (Daylight on):
We fixed it in rev51.7
I have one more issue after update. OUT5 AND OUT6 stopped working as analog outputs. In last working version i know ver. 46.2. In my setup this analog outputs (OUT5 OUT6) send analog signal to VAV (10v-100%). Return signal from VAV shows actual airflow (IN1 IN2). After update OUT5 and OUT6 stops working as AO.
Downgrade to 46.2:
In normal conditions output is controlled by program and schedule. After update it stopped working. For testing i turned programs off and tried to entered AO - 10v manually. Unfortunately after entering 10 to OUT5 & OUT6, it goes back automatically to 0.00.